The heating system is constantly losing pressure what should I do?
If you are constantly losing pressure in the heating system you could try the following to establish the cause by:
Checking all visible joints including radiator valves and connections for obvious signs of leakage. There needs to be consideration to potential leaks to any under-floor pipe work.
Check that there is no water being discharged from the pressure relief valve (sometimes referred to as an overflow). This pipe usually goes from the boiler through to an outside wall and terminates outside. Check this for signs of dripping. If it is wet, this may mean that the pressure relief valve is faulty.
In either case, if your heating system keeps losing pressure to gain advice or help you should:
- Contact your installer
- Contact your local Worcester Accredited Installer
- Call our Contact Centre on 014940099
More All FAQs
- Have you got more information on how to wire controls to your range of Greenstar gas boilers?
- How many immersion heaters do you have in your cylinders?
- What are the kW outputs of the coils inside Worcester cylinders?
- Is the GB162 flue system suitable to be ran externally?
- Do I have to use the GB162 pump group or can I fit my own pump on the system?
- Does the Heat Interface Unit require a permanent live?
- Does the Heat Interface Unit require a flue to be fitted?
- Can I use a secondary return with the Greenspring water heater?
- I am installing a GB162 can I used external 240vac controls to operate the boiler?
- Can I use a BMS system with a 0 - 10 volt signal to control the GB162?