How often should I need to top up the pressure in the heating system?
When the heating system is cool, the pressure should be between 1 and 1.5 bar on the pressure gauge (the indicator needle would usually be in the green section). If pressure is below 0.5 bar (down in the red section), water has been lost from the system and must be replaced. Note: The red part of the dial could also indicate the pressure being too high (about 2.75 bar or more). If the pressure gauge indicates high pressure as a result of over filling, you will need to bleed a radiator until the pressure gauge returns between 1 and 1.5 bar.
If pressure rises by more than 1 bar when the heating is up to temperature then the expansion vessel may require repressurising. This will require a service engineer. The pressure in the system will usually require topping up once or twice a year. If you are having to repressurise your heating system much more frequently, please contact your installer.
More All FAQs
- How do I know that my condensate pipe is blocked?
- My boiler is producing a 'gurgling' sound what could be the cause?
- What is the lower limit operating temperature of a Worcester air to water heat pump?
- What are the key maintenance requirements for Greensource Air to Water Heat Pumps?
- How should the air to water heat pump unit be sited to ensure the airflow and access it needs?
- What size of cable should be used to connect the air to water heat pump to the mains electricity supply?
- How cost effective are solar thermal panels?
- Is there enough sunshine in the UK for solar thermal?
- What is the best way to calculate how many solar thermal panels I need?
- Is planning permission required for solar thermal panels?